|Hotels ,Motels ,Equipments, Instrumentation
Instrumentation and Control
Thermometers and pressure gauges shall be installed in
the air, water, steam and fuel oil systems for balancing,
operating and maintenance purposes.
Proper recording devices and integrating steam flow meters
shall be installed in the major steam systems such as: boiler
header, absorption refrigeration machines and domestic hot
Proper recording meters shall be installed for chilled
and condenser water circuits of the refrigeration system.
Meters are to record temperatures in and out and flow in
A remote alarm indication panel shall be installed in
the Engineer's Office.
An oil totalising meter shall be installed in fuel oil
Stack thermometers shall be installed in all stacks.
A portable combustion test kit to measure CO2 and O2 of
flue gas shall be furnished.
Draft gauges shall be installed at each air filter bank.
An outdoor wet bulb and dry bulb recorder shall be installed.
Water totalising meters shall be installed in make up
lines to cooling tower, boiler feed system, cooling tower
blow down, and irrigation system.
A contact pyrometer shall be furnished if the property
has steam systems.
A Building Management System shall be provided to supervise
and control the mechanical, electrical plumbing, fire protection
and security systems. Control for the mechanical systems
shall be by Direct Digital Control (DDC).